Capacity: 4MVA supply to site, max capacity
to site without additional infrastructure upgrade 9MVA. A+B Eaton switchgear using ABB breakers.
Feeds: A+B feeds from 2N UPS pairs to each rack
UPS: Eaton 9395 UPS 750kW max load, current capacity allocated to Data Hall 1 is 400kW, at Denco full load the battery autonomy is 5 mins
Generators: A+B 1250 kVA FG Wilson Generators, with belly tank storage for 24 hours at full load.
System: Denco DMF 65 units provide an efficient Combi-cool air flow in an N+1 Configuration.
Regulation: Intelligent management holding Optimum temperatures within ASHRAE range.
Air Handling: Data Hall cooling is N+1 with Denco downflow units (65kW each), using Combi-cool technology.
Monitoring: Secure operations room which monitors CCTV, BMS, Data Hall power, cooling and resiliency.
Access: State of the art access control with Bio-metrics throughout the facility.
Perimeter: A secure perimeter with two stage gated access and a state of the art CCTV.